In Metro systems everywhere, the EEH Emergency Egress Door provides passengers and crew with an auxiliary exit to the street level in emergency situations
Channel frame construction with anchors welded around the frame for casting into concrete.
Diamond plate door panel is reinforced for a live load of 300 pounds/sqft. (pedestrian loading or light vehicular loading for off-street locations)
EEH EMERGENCY EGRESS Floor Door Specifications:
Material: Cover and frame shall be mill finish aluminum. All hardware shall be 316 stainless steel.
Door: 1/4" Diamond plate door panel is reinforced for a live load of 300 pounds/sqft. (pedestrian loading or light vehicular loading for off-street locations) with flush steel lifting handles. Covers shall be equipped with 316 stainless steel hold-open arms with red vinyl grip to hold cover in the 90 degrees open position.
Frame: 3/8" aluminum channel that drains rainwater through a 1-1/2" pipe coupling.
Hinge:316 stainless steel with tamper resistant fasteners.
Spring:Stainless steel compression springs enclosed in telescoping tubes. Lower tube interlocks with spring support bracket welded to the door frame.
Latch: Two-point 316 stainless steel with interior push bar and exterior plug for fire department spanner.
Hand Rail: Aluminum tubing welded to each cover.
Signage: “Push Bar” and “Keep Clear” signs to be included.